1 Advanced Ventilation for Residential applications FBC Res Course Description Review of the Residential Ventilation requirements in the Florida Building Code, Residential 2010.
2 I. Introduction Dean Decker is a Certified Air Conditioning Contractor, Building Official, Mechanical Chief, Mechanical Plans Examiner, and Mechanical Inspector. Rolando Soto is a Professional Engineer, Certified Building Official, Mechanical Plans Examiner, and Mechanical Inspector
3 Florida Building Code Chapter 1
4 FBC Scope The provisions of this code shall apply to the construction, alteration, movement, enlargement, replacement, repair, equipment, use and occupancy, location, maintenance, removal and demolition of every building or structure or any appurtenances connected or attached to such buildings or structures.
5 Exceptions: 1. Detached one- and two-family dwellings and multiple single-family dwellings (townhouses) not more than three stories above grade plane in height with a separate means of egress and their accessory structures shall comply with the Florida Building Code, Residential. 2. Existing buildings undergoing repair, alterations or additions and change of occupancy shall comply with Chapter 34 of this code.
6 2010 Florida Building Code: Residential Chapter 1 - Scope and Administration R101.2 Scope. The provisions of the Florida Building Code, Residential shall apply to the construction, alteration, movement, enlargement, replacement, repair, equipment, use and occupancy, location, removal and demolition of detached one- and two-family dwellings and townhouses not more than three stories above grade plane in height with a separate means of egress and their accessory structures. Exceptions: 1. Live/work units complying with the requirements of Section 438 of the Florida Building Code, Building shall be permitted to be built as one- and two-family dwellings or townhouses. Fire suppression required by Section of the Florida Building Code, Building when constructed under the Florida Building Code, Residential shall conform to Section of the Florida Building Code, Building. 2. Existing buildings undergoing repair, alteration or additions, and change of occupancy shall comply with the Florida Building Code, Existing Building.
7 FBC Intent. R The provisions of Chapter 1, Florida Building Code, Building, shall govern the administration and enforcement of the Florida Building Code, Residential. The purpose of this code is to establish the minimum requirements to safeguard the public health, safety and general welfare through structural strength, means of egress facilities, stability, sanitation, adequate light and ventilation, energy conservation, and safety to life and property from fire and other hazards attributed to the built environment and to provide safety to fire fighters and emergency responders during emergency operations.
8 FBC R Chapter 3 - Building and Planning SECTION R303 LIGHT, VENTILATION AND HEATING R303.1 Habitable rooms. All habitable rooms shall have an aggregate glazing area of not less than 8 percent of the floor area of such rooms. Natural ventilation shall be through windows, doors, louvers or other approved openings to the outdoor air. Such openings shall be provided with ready access or shall otherwise be readily controllable by the building occupants. The minimum openable area to the outdoors shall be 4 percent of the floor area being ventilated.
9 Exceptions: 1. The glazed areas need not be openable where the opening is not required by Section R310 and an approved mechanical ventilation system capable of producing 0.35 air change per hour in the room is installed or a whole-house mechanical ventilation system is installed capable of supplying outdoor ventilation air of 15 cubic feet per minute (cfm) (78 L/s) per occupant computed on the basis of two occupants for the first bedroom and one occupant for each additional bedroom. 2. The glazed areas need not be installed in rooms where Exception 1 above is satisfied and artificial light is provided capable of producing an average illumination of 6 footcandles (65 lux) over the area of the room at a height of 30 inches (762 mm) above the floor level. 3. Use of sunroom additions and patio covers, as defined in Section R202, shall be permitted for natural ventilation if in excess of 40 percent of the exterior sunroom walls are open, or are enclosed only by insect screening.
10 R303.2 Adjoining rooms. For the purpose of determining light and ventilation requirements, any room shall be considered as a portion of an adjoining room when at least one-half of the area of the common wall is open and unobstructed and provides an opening of not less than one-tenth of the floor area of the interior room but not less than 25 square feet (2.3 m 2 ). Exception: Openings required for light and/or ventilation shall be permitted to open into a thermally isolated sunroom addition or patio cover, provided that there is an openable area between the adjoining room and the sunroom addition or patio cover of not less than one-tenth of the floor area of the interior room but not less than 20 square feet (2 m 2 ). The minimum openable area to the outdoors shall be based upon the total floor area being ventilated.
11 R303.3 Bathrooms. Bathrooms, water closet compartments and other similar rooms shall be provided with aggregate glazing area in windows of not less than 3 square feet (0.3 m 2 ), one-half of which must be openable. Exception: The glazed areas shall not be required where artificial light and a mechanical ventilation system are provided. The minimum ventilation rates shall be 50 cubic feet per minute (24 L/s) for intermittent ventilation or 20 cubic feet per minute (10 L/s) for continuous ventilation. Ventilation air from the space shall be exhausted directly to the outside.
12 Natural ventilation provided
13 Where do I wash my hands?
14 R303.4 Opening location. R303.4 Opening location. Outdoor intake and exhaust openings shall be located in accordance with Sections R and R R Intake openings. Mechanical and gravity outdoor air intake openings shall be located a minimum of 10 feet (3048 mm) from any hazardous or noxious contaminant, such as vents, chimneys, plumbing vents, streets, alleys, parking lots and loading docks, except as otherwise specified in this code. Where a source of contaminant is located within 10 feet (3048 mm) of an intake opening, such opening shall be located a minimum of 2 feet (610 mm) below the contaminant source. For the purpose of this section, the exhaust from dwelling unit toilet rooms, bathrooms and kitchens shall not be considered as hazardous or noxious. R Exhaust openings. Exhaust air shall not be directed onto walkways.
15 You are failing my inspection?! I even fire caulked around the duct!!!
16 R303.5 Outside opening protection. Air exhaust and intake openings that terminate outdoors shall be protected with corrosion-resistant screens, louvers or grilles having a minimum opening size of 1 / 4 inch (6 mm) and a maximum opening size of 1 / 2 inch (13 mm), in any dimension. Openings shall be protected against local weather conditions. Outdoor air exhaust and intake openings shall meet the provisions for exterior wall opening protectives in accordance with this code.
17 SECTION R309 GARAGES AND CARPORTS R309.1 Floor surface. Garage floor surfaces shall be of approved noncombustible material. The area of floor used for parking of automobiles or other vehicles shall be sloped to facilitate the movement of liquids to a drain or toward the main vehicle entry doorway. R309.2 Carports. Carports shall be open on at least two sides. Carport floor surfaces shall be of approved noncombustible material. Carports not open on at least two sides shall be considered a garage and shall comply with the provisions of this section for garages. Exception: Asphalt surfaces shall be permitted at ground level in carports. The area of floor used for parking of automobiles or other vehicles shall be sloped to facilitate the movement of liquids to a drain or toward the main vehicle entry doorway. R309.3 Flood hazard areas. For buildings located in flood hazard areas as established by Table R301.2(1), garage floors shall be: 1. Elevated to or above the design flood elevation as determined in Section R322; or 2. Located below the design flood elevation provided they are at or above grade on at least one side, are used solely for parking, building access or storage, meet the requirements of Section R322 and are otherwise constructed in accordance with this code. R309.4 Automatic garage door openers. Automatic garage door openers, if provided, shall be listed in accordance with UL 325. ( Note there is no mention of ventilation)
18 M Hydrogen generating and refueling operations. Ventilation shall be required in accordance with Section M , M or M in private garages that contain hydrogen-generating appliances or refueling systems. For the purpose of this section, rooms or spaces that are not part of the living space of a dwelling unit and that communicate directly with a private garage through openings shall be considered to be part of the private garage.
19 Hydrogen refueling
20 M Natural ventilation. Indoor locations intended for hydrogen-generating or refueling operations shall be limited to a maximum floor area of 850 square feet (79 m 2 ) and shall communicate with the outdoors in accordance with Sections M and M The maximum rated output capacity of hydrogen generating appliances shall not exceed 4 standard cubic feet per minute (1.9 L/s) of hydrogen for each 250 square feet (23 m 2 ) of floor area in such spaces. The minimum cross-sectional dimension of air openings shall be 3 inches (76 mm). Where ducts are used, they shall be of the same cross-sectional area as the free area of the openings to which they connect. In those locations, equipment and appliance shaving an ignition source shall be located so that the source of ignition is not within 12 inches (305 mm) of the ceiling.
21 M Two openings. Two permanent openings shall be constructed within the garage. The upper opening shall be located entirely within 12 inches (305 mm) of the ceiling of the garage. The lower opening shall be located entirely within 12 inches (305 mm) of the floor of the garage. Both openings shall be constructed in the same exterior wall. The openings shall communicate directly with the outdoors and shall have a minimum free area of 1 / 2 square foot per 1,000 cubic feet (1.7 m 2 /1000 m 3 ) of garage volume. M Louvers and grilles. In calculating free area required by Section M , the required size of openings shall be based on the net free area of each opening. If the free area through a design of louver or grille is known, it shall be used in calculating the size opening required to provide the free area specified. If the design and free area are not known, it shall be assumed that wood louvers will have a 25-percent free area and metal louvers and grilles will have a 75-percent free area. Louvers and grilles shall be fixed in the open position.
22 Did you finish the ducts in that attic?
23 M Mechanical ventilation. Indoor locations intended for hydrogen-generating or refueling operations shall be ventilated in accordance with Section of the Florida Building Code, Mechanical. In these locations, equipment and appliances having an ignition source shall be located so that the source of ignition is below the mechanical ventilation outlet(s). M Specially engineered installations. As an alternative to the provisions of Sections M and M , the necessary supply of air for ventilation and dilution of flammable gases shall be provided by an approved engineered system.
24 BORA Inspectors Vehicle
25 Chapter 15 - Exhaust Systems M Outdoor discharge. The air removed by every mechanical exhaust system shall be discharged to the outdoors. Air shall not be exhausted into an attic, soffit, ridge vent or crawl space. Exception: Whole-house ventilation-type attic fans that discharge into the attic space of dwelling units having private attics shall be permitted.
26 SECTION M1502 CLOTHES DRYER EXHAUST M Length identification. Where the exhaust duct is concealed within the building construction, the equivalent length of the exhaust duct shall be identified on a permanent label or tag. The label or tag shall be located within 6 feet (1829 mm) of the exhaust duct connection. M Exhaust duct required. Where space for a clothes dryer is provided, an exhaust duct system shall be installed. Where the clothes dryer is not installed at the time of occupancy the exhaust duct shall be capped or plugged in the space in which it originates and identified and marked "future use. Exception: Where a listed condensing clothes dryer is installed prior to occupancy of the structure. M Protection required. Protective shield plates shall be placed where nails or screws from finish or other work are likely to penetrate the clothes dryer exhaust duct. Shield plates shall be placed on the finished face of all framing members where there is less than 1 1 / 4 inches (32 mm) between the duct and the finished face of the framing member. Protective shield plates shall be constructed of steel, shall have a minimum thickness of inch (1.6 mm) and shall extend a minimum of 2 inches (51 mm) above sole plates and below top plates.
28 SECTION M1503 RANGE HOODS M General. Range hoods shall discharge to the outdoors through a single-wall duct. The duct serving the hood shall have a smooth interior surface, shall be air tight and shall be equipped with a backdraft damper. Ducts serving range hoods shall not terminate in an attic or crawl space or areas inside the building. Exception: Where installed in accordance with the manufacturer s installation instructions, and where mechanical or natural ventilation is otherwise provided, listed and labeled ductless range hoods shall not be required to discharge to the outdoors. M Duct material.
29 SECTION M1504 INSTALLATION OF MICROWAVE OVENS M Installation of a microwave oven over a cooking appliance. The installation of a listed and labeled cooking appliance or microwave oven over a listed and labeled cooking appliance shall conform to the terms of the upper appliance s listing and label and the manufacturer s installation instructions. The microwave oven shall conform to UL 923.
30 SECTION M1505 OVERHEAD EXHAUST HOODS M General. Domestic open-top broiler units shall have a metal exhaust hood, having a minimum thickness of inch ( mm) (No. 28 gage) with 1 / 4 inch (6.4 mm) clearance between the hood and the underside of combustible material or cabinets. A clearance of at least 24 inches (610 mm) shall be maintained between the cooking surface and the combustible material or cabinet. The hood shall be at least as wide as the broiler unit, extend over the entire unit, discharge to the outdoors and be equipped with a backdraft damper or other means to control infiltration/exfiltration when not in operation. Broiler units incorporating an integral exhaust system, and listed and labeled for use without an exhaust hood, need not have an exhaust hood.
31 SECTION M1506 EXHAUST DUCTS M Ducts. Where exhaust duct construction is not specified in this chapter, construction shall comply with Chapter 16.
32 SECTION M1507 MECHANICAL VENTILATION M General. Where toilet rooms and bathrooms are mechanically ventilated, the ventilation equipment shall be installed in accordance with this section. M Recirculation of air. Exhaust air from bathrooms and toilet rooms shall not be recirculated within a residence or to another dwelling unit and shall be exhausted directly to the outdoors. Exhaust air from bathrooms and toilet rooms shall not discharge into an attic, crawl space or other areas inside the building. M Ventilation rate. Ventilation systems shall be designed to have the capacity to exhaust the minimum air flow rate determined in accordance with Table M
33 TABLE M MINIMUM REQUIRED EXHAUST RATES FOR ONE- AND TWO-FAMILY DWELLINGS Kitchens AREA TO BE VENTILATED Bathrooms Toilet Rooms VENTILATION RATES 100 cfm intermittent or 25 cfm continuous Mechanical exhaust capacity of 50 cfm intermittent or 20 cfm continuous
34 Ok, we ll have to start from the beginning
35 Questions and comments. Course # Instructor: D. Decker, R. Soto
Study Session 3 2012 IRC Sections R303 R310 Building Planning II OBJECTIVE: To develop an understanding of the health and safety criteria of the code, including light and ventilation; minimum room areas
RESIDENTIAL BUILDING REQUIREMENTS Residential Building Requirements This is an informational booklet with some of the general residential construction requirements taken from the codes adopted by Campbell
CHECKLIST Inspecting a Garage By Ben Gromicko This section deals with the details of the garage or carport inspection that may be performed. At the end of this section, you shall be able to: describe the
Pre-Inspection Checklist INTRODUCTION: This pre-inspection checklist has been produced to assist you in preparing for a Continuing Certificate of Occupancy (CCO) inspection. The inspection criteria and
Revised 11/29/06 Knox County Residential Building Codes Significant Changes From The 1995 CABO One And Two Family Dwelling Code To The 2006 International Residential Code All one and two family dwellings
WASHINGTON STATE BUILDING CODE CHAPTER 51-51 WAC INTERNATIONAL RESIDENTIAL CODE 2015 Edition Washington State Building Code Council Copies of the State Building Codes and complete copies of the 2015 International
1 Development Services Department Building Permit & Inspection Services Basement Renovation Guide For Residential Dwellings This document is a guide for home owners and does not cover all possible conditions.
City and County of San Francisco Department of Building Inspection Edwin M. Lee, Mayor Tom C. Hui, S.E., C.B.O., Director Legalization of Dwelling Units Installed Without a Permit SCREENING FORM No fee
NEW HOMES PROGRAM 2017 PROGRAM GUIDE Focus on Energy, Wisconsin utilities statewide program for energy efficiency and renewable energy, helps eligible residents and businesses save energy and money while
TOWN OF ROTTERDAM RESIDENTIAL BUILDING PERMIT APPLICATION 355-7575 Ext. 395 Needed to Obtain Permit: 1. Building Permit Application, and/or residential plumbing permit application, as applicable, to be
Slab on Grade & Basements: A capillary break is installed on top of all footings Slab / Pre-Drywall / Thermal Inspection A minimum of 4" of clean or washed gravel (0.5" diameter or greater) is placed over
Chapter 4-16 SPECIAL DESIGN STANDARDS FOR TYPE V CONSTRUCTION Sections: 4-16-01 PURPOSE 4-16-02 APPLICABLE AREA 4-16-03 CONSTRUCTION AND OCCUPANCY 4-16-04 UPPER BUILDING AREA, HEIGHT, NUMBER OF STORIES
Residential Accessory Structures & Room Additions Planning and Development Services Department Building Safety Division 8500 Santa Fe Drive Overland Park, KS 66212 (913) 895-6225 Fax (913) 895-5016 Email:
Chapter 2: Foundation Crawlspace [V502.1.2] [V502.1.2] [V502.1.3] Vents. Vents in the crawlspace help keep floor insulation and floor framing dry. Crawlspace vents also reduce the potential for radon buildup
Natural Gas Service Installation and Meter Clearance Requirements Call SJG s new construction line at 1-844-611-5605 for more information. Builder/Owner/Developer Requirements The clearances in this handout
One and Two Family Additions An addition to a house, duplex, garage, or an accessory structure requires a building permit prior to performing any construction. Building Department & Permit Office Mon-Fri
K. B. FERRIE, CDR, Chief, Hull Division Purpose: This Plan Review Guideline (PRG) explains the requirements for seeking plan approval of ventilation systems from the Marine Safety Center (MSC) for most
BUILDING CODES & DESIGN CRITERIA Adopted Building Codes: 2006 International Building Code (IBC) 2006 International Residential Code (IRC) 2006 International Mechanical Code (IMC) 2006 International Plumbing
Fairfax County, Virginia Typical Finished Basement Details Based on the 2009 International Residential Code CONTENTS General Requirements... 2 Emergency Escape and Rescue... 2 Wall Construction... 3 Floor/ceiling
Building Codes and Ordinances ARC 227 Week 6 Fire Resistive Construction 03.02.10 Instructor: Rick Staub, AIA Email: email@example.com Phone: 860-434-7707 Fire Resistive Construction Passive
This information must be on the drawing documents not attached to plans. The following Compliance statements must be on the drawings: 2009 International Energy Conservation Code Statement of acknowledgement
Floor Plan Symbols Floor Plan *The floor plan represents a section view of a residence which has had an imaginary cut made approximately 4 feet above the floor line. *Residential floor plans are generally
2003 International Residential Building Code Section R305 Ceiling Height Habitable rooms, hallways, corridors, bathrooms, toilet rooms, laundry rooms and basements shall have a ceiling height of not less
2008 NEC Guide Lines for Home Owner Doing Electrical Work on their Property A brief summary of the most used code references for residential wiring State of Idaho Division of Building Safety Electrical
I N D E X E d u c a t i o n a l S e m i n a r s f o r B u i l d i n g & R e s i d e n t i a l C o d e Title Course Number *Seminar Length (days) Pg. Class Scheduling Policies 8 International Building Code
CITY OF WENTZVILLE RESIDENTIAL CODE PLAN REVIEW CHECK LIST Items indicated with an X are to be addressed by incorporation into revised plans. A checkmark indicates O.K. Date: Lot # Subdivision: Address:
LUMBER & MILLWORK Excerpts from: International Residential Code 2009 R310.1 Emergency escape and rescue required. Basements, habitable attics and every sleeping room shall have at least one operable emergency
2001 National Workshop on State Building Energy Codes July 16-19 th, 2001 Burlington, Vermont A Systems Engineering Approach to the Design of Energy and Resource Efficient Homes Presented By: Mark LaLiberte
Building Regulations; Construction 11 b. Ceilings or roofs shall have a minimum of an "R" factor of 12; and c. Where the roof serves also as the finished ceiling a vent space of two inches shall be required
The Inspection Process In Waxhaw N.C. This information is provided by the Waxhaw Enforcement Division to assist you in the progression of your project. Nothing in this document should be considered "Code"
19 SECTION 3 NATURAL VENTILATION 3.1 SCOPE OF SECTION This Section specifies the means of achieving the quantity of outdoor air required in a naturally ventilated enclosure. The provisions described include
2016 CALGREEN RESIDENTIAL CHECKLIST MANDATORY ITEMS City of San Carlos - Building Division 600 Elm Street, San Carlos, CA 94070 Phone: 650-802-4261 PURPOSE: The residential provisions of the 2016 CalGreen
ASHRAE 62.2: What s New in 2016 Rick Karg 2016 Residential Energy Dynamics, LLC What We Will Talk About Overview of mechanics of 62.2-2016. Logic behind the Standard. Sizing local ventilation (exhaust-only).
Chapter 17 Private Potable Water Supply Systems 17.1 GENERAL REGULATIONS 17.1.1 Applicability The regulations in this chapter apply to any private potable water supply system where plumbing fixtures are
General Information Site Card. Before starting construction, post the site card (issued by the City) in a front window visible from the street. Miss Dig. Before you dig, call Miss Dig at 800.482.7171 This
REQUIREMENTS FOR SUBSTANTIALLY DAMAGED AND SUBSTANTIALLY IMPROVED STRUCTURES If your home or business incurred damage, the engineering department, in conjunction with the Flood Mitigation Officer, will
Permit Requirements: Any owner, authorized agent, or contractor who desires to construct, enlarge, alter, repair, move, demolish, or change the occupancy of a building or structure, or to erect, install,
Applying the Building Code During Design A Step-By-Step Process AIA Learning Units The Salt Lake City CSI Chapter is a Registered Provider with The American Institute of Architects Continuing Education
BUILDING A STRUCTURE IN THE FLOODPLAIN When you apply for a zoning permit to build a home or other structure and it is determined your land is in the floodplain, the following procedures will apply: 1.
Section 6 Radon Vent Pipe Labeling Performance Indicators Radon Vent Pipe System Connected after sub-grade system installed Pipe cannot be trapped Provide space in chases Support at each floor level Discharge
Milk and Dairy Food Safety Branch 1220 N Street, Sacramento, CA 95814 GUIDELINES FOR SANITARY DESIGN AND CONSTRUCTION OF MILK PRODUCTS PLANTS (rev. 10-20-2011) The outline below lists sanitary requirements
Universal Design Standards For applications submitted and approved after April 16, 2007 Introduction to Universal Design Universal design is a building concept that incorporates products, general design
SECTION 500.110: FIRE WALL AND FIRE SUPPRESSION REGULATIONS FOR R1-Z, R-2, R-3 ZONING AND PDD CATEGORIES A. Purpose. The intent of this regulation is to amend the current adopted edition of the International
CITY OF CRANSTON RESIDENTIAL PERMIT PROCEDURE BASEMENT RENOVATION WE WILL NOT ACCEPT ANY PLANS OR PAPERWORK TO START THE REVIEW PROCESS UNTIL ALL ITEMS BELOW ARE SUBMITTED TO US AT THE SAME TIME. PLANS
CHAPTER 3 PRESCRIPTIVE COMPLIANCE METHOD [B] SECTION 301 GENERAL 301.1 Scope. The provisions of this chapter shall control the alteration, repair, addition and change of occupancy of existing structures,
This list is provided as a guide to help you understand the information that must be contained on the construction drawings. This list is not all-inclusive of all building codes but is used as a general
CHAPTER 8 INTERIOR FINISHES SECTION 801 GENERAL 801.1 Scope. Provisions of this chapter shall govern the use of materials used as interior finishes, trim and decorative materials. 801.2 Interior wall and
Minnesota Healthcare Engineers Association, Fall Conference Bob Dehler, P.E. Engineering Program Manager September 14, 2017 Categories of Rehabilitation Work in Healthcare Facilities Bob Dehler, P.E. firstname.lastname@example.org
Crawl Space Moisture Control Crawl space foundations are found in many homes. Typically, these foundation types are equipped with operable vents designed to provide ventilation for moisture control. Unfortunately,
HERMIT S REST GRAND CANYON NATIONAL PARK BUILDING CODE REVIEW 27 September 2007 prepared by: J. CHRIS EVANS ARCHITECT 3220 E. Terra Alta Blvd. No. 9 Tucson, Arizona 85716 520.319.8835 email@example.com
The following regulations pertain to Building Division requirements for the plan review, approval and inspection of marijuana-related occupancies. The requirements listed below are only intended to assist
City of Twin Falls Building Department 324 Hansen Street East P.O. Box 1907 Twin Falls, ID 83303-1907 208-735-7238 208-736-2256 www.tfid.org PROJECT INFORMATION Project Residential Building Permit Application
Chapter 23.12 UNIFORM CODES FOR CONSTRUCTION BUILDING CODE 23.12.010 Adoption of the 2010 California Building Code. Part 2. Title 24 of the California Code of Regulations. There is adopted and incorporated
1.0 INDEX 1.0 INDEX 2.0 SCOPE 3.0 GENERAL REQUIREMENTS 4.0 EQUIPMENT 5.0 METER REQUIREMENTS 6.0 METER FACILITIES 7.0 ELECTRICAL CONNECTIONS 2.0 SCOPE This guide covers general requirements and codes for
HCM-00952 UNIVERSITY OF ALASKA FAIRBANKS UNIVERSITY OF ALASKA FAIRBANKS Building Challenges in Alaska INTRODUCTION Special considerations for building in Alaska are recommended that are normally not included
Inspection Report Dayvolt's Home Inspections L.L.C. Date&Time of Inspection: 5/9/17, 12:10 PM Inspector's Name: Dustin Dayvolt Building Address: Sample City: State: Zip Code: Type of property inspected:
AGREEMENT CONCERNING EXISTING AS BUILT CONSTRUCTION Building Permit Number: Date Received: By: I,, as owner of record of the above property, hereby request a permit for and final inspection of the installation
ASHRAE 62.2-2013 and Indoor Air Quality Weatherize Ohio Conference October 27 29, 2015 The State of Ohio is an Equal Opportunity Employer and Provider of ADA Services Introduction ASHRAE: Why is it needed?
Inspection Services CITY OF GRANDE PRAIRIE HOMEOWNER S PERMIITS AND WIRING GUIDE FOR ELECTRICAL INSTALLATIONS 2016 INDEX Page Applying for an Electrical Permit 3 Permit Application Requirements 3 Permit
CHAPTER 8 INTERIOR FINISHES SECTION 801 GENERAL 801.1 Scope. Provisions of this chapter shall govern the use of materials used as interior finishes, trim and decorative materials. 801.2 Interior wall and
CHAPTER 5: RESIDENTIAL USE DEVELOPMENT STANDARDS ARTICLE 1: SINGLE FAMILY 305-01. Application The provisions of this Article shall apply to the following uses in any zone: (e) (f) One (1) single family
Kelly Village Apartments 3118 Green Houston, Texas 77020 Houston Housing Authority J. Allen Management Managing Agent Scope for Kelly Village Unit #1125 Overall Scope: Demolition, Renovation, and Restoration
FEMA 50% RULE - SUBSTANTIAL IMPROVEMENT SUBSTANTIAL IMPROVEMENT/DAMAGE Z101-0410 NOTICE TO PROPERTY OWNERS Rebuilding your Home after the storm? Adding on, renovating, or remodeling your home? Here's information
CONSTRUCTION CODE PERMIT INFORMATION INTRODUCTION The Lebanon County Planning Department is a Pennsylvania Certified 3 rd Party Inspection Agency. The Lebanon County Planning Department is under contract
DRAFT 2.7 (9/26/16) Port Townsend EcoVillage Tiny House Requirements Please note that the following requirements are a work in progress, many of which are particular to the PT ecovillage. Once finalized,
Top 10 Defects Found in New Homes Presented by The National Association of Certified Home Inspectors Chicago Chapter - The National Association of Certified Home Inspectors 1 Top 10 New Home Defects New
Basement Guide www.douglas.co.us FINISHED BASEMENT REQUIREMENT GUIDE Current Codes: 2012 International Residential Code 2009 International Energy Conservation Code 2014 National Electrical Code 2012 I-Code
SPECIFICATIONS FOR FIELD LABORATORIES 180. 1. SCOPE These Specifications govern all requirements for supplying and maintaining a field laboratory for the exclusive use of the Engineer. 2. SUPPLY The Contractor
24 hour inspection line 737.793.1656 Date CERTIFICATE of OCCUPANCY APPLICATION RESIDENTIAL 1. Building Information Property address Property ID Type of Housing (please circle): OWNER OCCUPIED RENTAL HOME
Know Thy Codes! The Building Codes Building Codes The Code of Hammurabi 4000bc Developed 19 th and 20 th c. Codes define what you can and can t do Allowable area and height based on degree of danger Fire
CITY OF CAMDENTON OFFICE OF THE BUILDING OFFICIAL Commercial Building & Architectural Review Permit Application DATE: / / PERMIT # REQUEST FOR: NEW BUILDING ADDITION REMODEL PLUMBING ONLY ELECTRIC ONLY
PREP + INSULATION HOME ENERGY UPGRADES What every contractor needs to know. Copyright 2012 Advanced Energy. All Rights Reserved 103 HOME ENERGY UPGRADES Prep + Insulation Contents Air sealing is a challenging
CHAPTER 7 FIRE AND SMOKE PROTECTION FEATURES SECTION 70 GENERAL 70. Scope. The provisions of this chapter shall govern the materials, systems and assemblies used for structural fire resistance and fire-resistance-rated
LEED v4 for Homes, Residential Project Summary and Checklist One and Two Family New Construction Summary Date of Application Path Project Project Address Owner Architect Third Party Third Party Provider
City of Aurora Public Works Department AURORA PUBLIC SCHOOLS AND CHERRY CREEK PUBLIC SCHOOLS 2014 Commercial Plan Submittal Checklist Permit Center 15151 E. Alameda Parkway, Ste 2400 Aurora, CO 80012 303-739-7420