1 202 IBC 75 TABLES 75.3 Marking Rated Glazing Assemblies 75.4 Opening Protection Assemblies, Ratings and Markings 75.5 Window Assembly Protection Ratings These Tables represent the code changes approved by ICC at the 202 IBC Code hearings. The final published version of 202 IBC 75 Tables will be available on April 20. The recommended product found in these tables are not part of the 202 IBC, but provided by SAFTI FIRST as guide for choosing and specifying the correct code approved product
2 202 IBC Table 75.3 (New) Marking -Rated Glazing Assemblies Test Standard Marking Definition of Marking Recommended Product (not in IBC added for easy reference) ASTM E9 or UL 263 W Meets wall assembly criteria. -20 NFPA 257 or UL 9 OH Meets fire window assembly criteria including the hose stream test. PYRAN Platinum by by PYRAN Platinum L by NFPA 252 or UL 0B or UL 0C D Meets fire door assembly criteria. -20 by PYRAN Platinum L by H Meets fire door assembly Hose Stream test. -20 by PYRAN Platinum L by T Meets 450º F temperature rise criteria for 30 minutes -20 XXX The time in minutes of the fire resistance or fire protection rating of the glazing assembly The time in minutes of the fire resistance or fire protection rating of the glazing assembly
3 202 IBC Table 75.4 (rev. 75.5) Opening Protection Assemblies, Ratings and Markings TYPE OF REQUIRED WALL RATING (HRS.) MINIMUM FIRE DOOR AND FIRE SHUTTER RATING (HRS.) DOOR VISION PANEL SIZE FIRE RATED GLAZING DOOR VISION PANEL e,d Recommended Product for Door Vision Panel (not in IBC added for easy reference) MINIMUM SIDELITE/TRANSOM RATING (HRS.) Protection Resistance FIRE RATED GLAZING SIDELITE/TRANSOM PANEL Protection Resistance Recommended SAFTI FIRST Product for Sidelite/Transom (not in IBC added for easy reference) W a 3 W-80 walls and fire barriers having a required fire resistance rating greater than hour 2 -/2 00 sq. in c -/2 -/2 00 sq. in c 2 -/2 W-20 W-90 SuperLite II-XL 20 Shaft, exit enclosures and exit passageway walls 2 -/2 00 sq. in c 00 sq. in c = D-H-T-90 or D-H-T-W-90 = D-H-60 = D-H-T-60 or D-H-T-W-60 2 W-20 SuperLite II-XL 20 W-60
4 Other Barriers 3/4 D-H-NT-45 3/4 D-H-45 and L by Partitions / Corridor Walls /3 b 0.5 /3 b 3/4 b / and L by and L by Other Partitions 3/4 0.5 /3 D-H-45 D-H-20 3/4 D-H-45 /3 D-H-20 and L by and L by 3 -/2 00 sq. in. c 3 W-80 Exterior Walls 2 -/2 00 sq. in. c 2 W-20 SuperLite II-XL 20 3/4 D-H-45 3/4 D-H-NT-45 and L by Smoke Barriers /3 b 3/4 45 and L by a. Two doors, each with a fire protection rating of -/2 hours, installed on opposite sides of the same opening in a fire wall, shall be deemed equivalent in fire protection rating to one 3-hour fire door. b. For testing requirements, see Section c. resistance rated glazing tested to ASTM E9 per section 75.2 shall be permitted, in the maximum size tested. d. Under the column heading rated glazing marking door vision panel, W refers to the fire-resistance rating of the glazing, not the frame.
5 202 IBC Table 75.5 (rev. 75.6) Window Assembly Protection Ratings TYPE OF WALL Interior walls walls barriers REQUIRED WALL RATING (hours) All > MINIMUM FIRE WINDOW RATING (hours) FIRE RATED GLAZING Recommended Product (not in IBC added for easy reference) -20 Incidental use areas ( ), Mixed occupancy separations( ) If less than 25% of the wall area:,, PYRAN Platinum, or L by Smoke barriers and fire partitions Smoke barriers 0.5 /3 OH-20 or W-30 If less than 25% of the wall area:,, PYRAN Platinum, or L by Exterior walls > -/2 OH-90 or W-90 b 0.5 /3 OH-20 or W-30 If less than 25% of the wall area:,, PYRAN Platinum, or L by Party wall All NP Applicable NP a. permitted except fire resistance rated glazing assemblies tested to ASTM E9 or UL 263, as specified in Section 75.2 b. xxx = The fire rating duration period in minutes, which shall be equal to the fire resistance rating required for the wall assembly.