1 780 CMR: 9 th Edition Massachusetts State Building Code Presented to: BSA Codes Committee DATE: January 20, 2016
2 This course is registered with AIA CES for continuing professional education. Credit(s) earned on completion of this course will be reported to AIA CES for AIA members. Certificates of Completion for both AIA members and non-aia members are available upon request. Questions related to specific materials, methods, and services will be addressed at the conclusion of this presentation.
3 Course Overview Review impactful changes to the base language between the 2009 and 2015 I-Codes International Building Code 2015 International Existing Building Code 2015 International Mechanical Code 2015 International Energy Conservation Code 2013 ASHRAE Standard 90.1 Grace Period, no longer 2012 Jurisdictions
4 Chapter 1: Conflicting Provisions between Codes and Standards 2015 IBC Section Conflicts. Where conflicts occur between provisions of this code and referenced codes and standards, the provisions of this code shall apply Provisions in Referenced Codes and Standards. Where the extent of the reference to a referenced code or standard includes subject matter that is within the scope of this code or the International Codes listed in Section 101.4, the provisions of this code or the International codes listed in Section 101.4, as applicable, shall take precedence over the provisions in the referenced code or standard.
5 Chapter 1: Flood zones 2015 IBC Section Determination of substantially improved or substantially damaged existing buildings and structures in flood hazard areas. For applications for reconstruction, rehabilitation, repair, alteration, addition or other improvement of existing buildings or structures located in flood hazard areas, the building official shall determine if the proposed work constitutes substantial improvement or repair of substantial damage. Where the building official determines that the proposed work constitutes substantial improvement or repair or substantial damage and where required by this code, the building official shall require the building to meet the requirements of Section Section 1612 references Flood Loads. Substantially Improved and Substantially Damaged are defined in Chapter 2 and by Federal Regulations. A substantial improvement is work that equals or exceeds 50% of the market value of the building.
6 Chapter 1: Change of Use or Occupancy 2009 IBC Section No building or structure shall be used or occupied, and no change in the existing occupancy classification of a building or structure or portion thereof shall be made, until the building official has issued a certificate of occupancy therefore as provided herein IBC Section No building or structure shall be used or occupied, and no change in the existing use or occupancy classification of a building or structure or portion thereof shall be made, until the building official has issued a certificate of occupancy therefore as provided herein.
7 Chapter 4: Egress Travel Through an Atrium 2015 IBC Section Exit Access Travel Distance Egress not through an atrium shall comply with Section 1017 Egress through an atrium at the level of discharge shall comply with Section 1017 Egress through an atrium not at the level of discharge shall not exceed 200 feet Maximum of 50% of interior exit stairways are permitted to egress through an atrium on the level of discharge
8 Chapter 5: General Building Height and Area Limitations 2009 IBC General. The building height and area shall not exceed the limits specified in Table IBC General. Unless otherwise specifically modified in Chapter 4 and this chapter, building height, number of stories and building area shall not exceed the limits specified in Sections 504 and 506
9 Chapter 5: General Building Height and Area Limitations
10 Chapter 5: General Building Height and Area Limitations
11 Chapter 5: General Building Height and Area Limitations
12 Chapter 5: Incidental Uses-General Provisions 2009 IBC Separation of incidental accessory occupancies. The incidental accessory occupancies listed in Table shall be separated from the remainder of the building or be equipped with an automatic fire-extinguishing system, or both, in accordance with Table IBC General. Incidental uses located within single occupancy or mixed occupancy buildings shall comply with the provisions of this section. Incidental uses are ancillary functions associated with a given occupancy that generally pose a greater level of risk to that occupancy and are limited to those uses listed in Table 509.
13 Chapter 5: Incidental Uses-General Provisions
14 Chapter 5: Horizontal Building Separation 2009 IBC Section Condition 2. The building below the horizontal assembly is no more than one story above grade plane IBC Section Condition 2, which limits the height of the building below the horizontal assembly, is deleted.
15 Chapter 6 One-Hour Substitution Table 601, Footnote d: An approved automatic sprinkler system in accordance with Section shall be allowed to be substituted for 1-hour fire-resistance rated construction, provided such system is not otherwise required by other provisions of the code OR used for an allowable area increase in accordance with Section or an allowable height increase in accordance with Section The 1-hour substitution for the fire resistance of exterior walls shall not be permitted.
16 Chapter 7: Structural Stability of Fire Walls 2009 IBC Structural stability. Fire walls shall have sufficient structural stability under fire conditions to allow collapse of construction on wither side without collapse of the wall for the duration of time indicated by the required fireresistance rating IBC Structural Stability. Fire walls shall be designed and constructed to allow collapse of the structure on either side without collapse of the wall under fire conditions. Fire walls designed and constructed in accordance with NFPA 221 shall be deemed to comply with this section.
17 Chapter 7: Vertical Openings Vertical openings in Section 708 of the 2009 IBC have been moved to Section 712. There was a significant reformatting of vertical openings between the 2009 and 2012 IBC. The code now places an emphasis on the presence of vertical openings rather than on shaft enclosures, recognizing that the use of shaft enclosures is just one of many acceptable protective measures that can be utilized to address the hazards related to vertical openings.
18 Chapter 7: Membrane Penetrations Section in 2009 IBC moved to Section in 2015 IBC and two exceptions are added: 6. Noncombustible items that are cast into concrete building elements and that do not penetrate both top and bottom surfaces of the element 7. The ceiling membrane of 1- and 2-hour fire-resistance-rated horizontal assemblies is permitted to be interrupted with the double wood top plate of a wall assembly that is sheathed with Type X gypsum wallboard, provided that all penetrating items through the double top plates are protected in accordance with Section or and the ceiling membrane is tight to the top plates.
19 Chapter 7: Ducts Transitioning between Shafts Section Ducts and Air Transfer Openings. Ducts transitioning horizontally between shafts shall not require a shaft enclosure provided that the duct penetration into each associated shaft is protected with dampers comply with this section. Ducts are now expressly allowed to exit a shaft, transition horizontally, and enter another shaft without continuous shaft construction.
20 Chapter 10: Reorganization KEY Yellow Reorganization Green Addition Blue Deletion
21 Chapter 10: Sections 1006 and 1007 Provisions in Sections 1014, 1015 and 1021 in the 2009 IBC relocated to Sections 1006 and 1007 in 2015 IBC. Provisions include: Numbers of exits and exit access doorways Exit and exit access doorway configuration
22 Chapter 10: Section Measurement Point. The separation distance required in Section shall be measured in accordance with the following: 1. The separation distance to exit or exit access doorways shall be measured to any point along the width of the doorway. 2. The separation distance to exit access stairways shall be measured to the closest riser. 3. The separation distance to exit access ramps shall be measured to the start of the ramp run.
23 Chapter 10: Stairs Exit Access Stairway. An interior stairway that is not a required interior exit stairway. Interior Exit Stairway. An exit component that serves to meet one or more means of egress design requirements, such as required number of exits or exit access travel distance, and provides for a protected path of egress travel to the exit discharge or public way.
24 Chapter 10: Stairway Extension 2009 IBC Extension. interior exit stairways and ramps are extended to an exit discharge or a public way by an exit passageway, the interior exit stairway and ramp shall be separated from the exit passageway by a fire barrier constructed in accordance with Section 707 or a horizontal assembly constructed in accordance with Section 711, or both IBC Exception 2. Separation between an interior exit stairway or ramp and the exit passageway extension shall not be required where there are no openings into the exit passageway extension.
25 Chapter 14: Water-Resistive Barriers 2015 IBC Section Vertical and lateral flame propagation. Exterior walls on buildings of Type I, II, III or IV construction that are greater than 40 feet (12,192 mm) in height above grade plane and contain a combustible waterresistive barrier shall be tested in accordance with and comply with the acceptance criteria of NFPA 285. For the purposes of this section, fenestration products and flashing of fenestration products shall not be considered part of the water-resistive barrier. Exceptions: Walls in which the water-resistive barrier is the only combustible component and: 1. The exterior wall has a wall covering of brick, concrete, stone, terra cotta, stucco or steel with minimum thicknesses in accordance with Table The water-resistive barrier has a Peak heat release rate < 150 kw/m 2 Total heat release < 20 MJ/m 2 Effective heat of combustion < 18 MJ/kg Flame spread index < 25 Smoke-developed index < 450
26 Chapter 30: Elevator Lobbies 2009 IBC Section Lobbies shall be provided where shaft enclosure connects >3 stories Lobby enclosure shall separate elevator shaft enclosure doors from each floor by fire partitions 2015 IBC Section 3006 Hoistway protection required where: No automatic sprinkler system Building contains Group I-1, I-2 or I-3 occupancy High-rise building with hoistway connecting >3 stories Hoistway protection includes: Enclosed elevator lobbies Additional door complying with Section Hoistway pressurization
27 Chapter 30: Standpipe Access 2009 IBC Standpipe Hose connection. A Class I standpipe hose connection in accordance with section 905 shall be provided in the exit enclosure having direct access from the fire service access elevator lobby IBC Standpipe Hose Connection. A Class I standpipe hose connection in accordance with section 905 shall be provided in the interior exit stairway and ramp having direct access from the fire service access elevator lobby Access. The exit enclosure containing the standpipe shall have access to the floor without passing through the fire service access elevator lobby
28 International Energy Conservation Code
29 2015 International Energy Conservation Code (IECC) Chapter 4 Commercial Energy Efficiency Section 401: General Section 402: Building Envelope Requirements Section 403: Building Mechanical Envelope Section 404: Service Water Heating Section 405: Electric Power and Lighting Systems Section 406: Additional Efficiency Package Options Section 407: Total Building Performance Section 408: System Commissioning
30 Section C401: General C401.2 Application Additional requirements of Section 406 Additional Energy Package Options have been added to the prescriptive compliance method Total Building Performance compliance method requires the building energy cost to be no more than 85% of the standard reference design building
31 Section C402: Building Envelope Requirements Table C Opaque Thermal Envelope Assembly Walls above grade: U-value for Metal Buildings change from to Heated Slabs: F-factor changes from 0.86 to from 0.65 Unheated Slabs: F-factor changes from 0.73 to from 0.54 C Fenestration Maximum Area Maximum Vertical fenestration area is limited to 30% (reduction from previous 40%) with increase to 40% when automatic daylight control is provided) C402.5 Air Leakage Thermal envelope Continues Air Barrier throughout the building thermal envelope requirement is now in the Code Fenestration air leakage criteria are established and testing standards are identified
32 Section C403: Building Mechanical Systems Table C Minimum Efficiency Requirements Increase in minimum efficiency requirements of the HVAC Equipment C Demand Controlled Ventilation Occupancy of the spaces requiring DCV is reduced from 40 to 25 people per 1000 SF C403.2.Energy Recovery Ventilation Systems No longer based on system capacity >5000 CFM and %% OA>70%. Now depends on annual hours of operation (< or > than 8000 hours), climate zone, system capacity and % of outside air. For ventilation systems operating over 8000 hours per year (i.e. residential ventilation) in Massachusetts energy recovery is required for ALL system capacities, with ANY %% of outside air C &2 Economizer Control Two-position economizer control is no longer allowed
33 Section C405: Electrical Power and Lighting Systems C405.1 Electric Power and Lighting Systems General In dwelling units in commercial buildings minimum number of lighting fixtures containing high efficiency lamps is increased from 50% to 75% C405.2 Lighting controls The lighting control requirements are significantly expanded Lighting Controls Required include Occupancy Sensors, Time Control, Daylight Responsive Controls, Accent Lighting Controls, Exterior Lighting Controls. C Daylight -Responsive Controls Except for healthcare and dwelling and sleeping units daylight responsive controls are required for all spaces with more than 150W of general lighting Excludes Decorative Lighting, Sleeping Areas, Patient Areas in Health Care
34 Section C405: Electrical Power and Lighting Systems C405.4 Interior Lighting Power Requirements A Space-by-space method of compliance is introduced in addition to the Building Area Method of compliance. LPD allowances have been reduced (i.e. Office Building went from 0.9 to 0.82 w/sf)
35 ASHRAE : Electrical Power and Lighting Systems Zones for exterior lighting are added. Garages required to have automatic shutoff and dimming
36 Section C405: Electrical Power and Lighting Systems Control requirements for exterior lighting.
37 Section C406: Additional Efficiency Package Options C406.1 Requirements Prescriptive compliance method will in addition require the building to comply with one of the following: Increase efficiency of HVAC equipment by 10% above minimum requirements Reduce LPD to 90% of code allowance Enhanced digital lighting controls Generate on-site renewable energy - no less than 0.5 watts per SF of conditioned area Dedicated Outdoor Air System (DOAS) with supply air temperature reset control High Efficiency Service Water heating no less than 60% of hot water requirements to be satisfied by waste heat recovery or solar water heating system
38 Section C407: Total Building Performance Total Building Performance compliance method requires the building energy cost to be no more than 85% of the standard reference design building
39 Section C407: Total Building Performance Example:
40 Section C407: Total Building Performance Example: Key ASHRAE Baseline Modeling Inputs ASHRAE Appendix G WWR 40% Glazing Type Double Pane U-Glass = 0.42 SHGC= 0.40 Mechanical System Floor by Floor Chilled Water VAV with Hot Water Heating LPD = 0.82 (Per ASHRAE ) Boiler 82% Efficient Chiller kw/ton Full Load and IPLV Miscellaneous Load (Office Power) 1.06 W/GSF
41 Section C407: Total Building Performance Example: FANS 10% Baseline HOT WTR 3% LIGHTS 20% PUMPS 8% COOLING 13% EQUIP 22% HEATING 24%
42 Section C407: Total Building Performance Example: Proposed Building Modeling Iterations Increase WWR 60% with ASHRAE Baseline Glass Improve Glazing Triple Pane (Viracon VE1-85) U-winter = 0.14 U-summer = 0.14 SHGC= 0.44 VT= 65% Condensing Boiler Plant 95% Seasonal Efficiency Magnetic Bearing (Or Equivalent) Chiller kw/ton Full load and IPLV Enthalpy Wheel Ventilation Air Energy Recovery 65% Efficiency Daylight Harvesting
43 Section C407: Total Building Performance Example:
44 Section C407: Total Building Performance Example: Energy Recovery Baseline
45 Section C407: Total Building Performance Example: Energy Recovery Baseline
46 Section C407: Total Building Performance Example: Energy Recovery Baseline
47 Section C407: Total Building Performance Example:
48 Section C408: System Commissioning The IECC nowrequires commissioning of the mechanical and electrical systems
49 International Mechanical Code
50 Chapter 2 International Mechanical Code 2009 IMC ENVIRONMENTAL AIR. Air that is conveyed to or from occupied areas through ducts which are not part of the heating or airconditioning system, such as ventilation for human usage, domestic kitchen range exhaust, bathroom exhaust, and domestic clothes dryer exhaust IMC ENVIRONMENTAL AIR. Air that is conveyed to or from occupied areas through ducts which are not part of the heating or airconditioning system, such as ventilation for human usage, domestic kitchen range exhaust, bathroom exhaust, domestic clothes dryer exhaust, and parking garage exhaust. Further clarifies that parking garage exhaust outlets can be 3 feet from a property line, 3 feet from operable windows and 10 feet from mechanical air intakes.
51 2015 International Mechanical Code (IMC) Equipment and Appliances on Roofs or Elevated Structures Permanent access is required to equipment and appliances on a roof or elevated structure higher than 16 feet above grade Ventilation Required Mechanical ventilation is required in the dwelling units if infiltration is less than 5 ACH when tested in accordance with IECC. Maximum envelope leakage allowed by IEEC is less than 0.4 CFM/SF which typically will results in less than 5 ACH. Mechanical ventilation implicitly is required for all residential dwelling units Intake Opening Locations Minimum clearance between an air intake opening and any public way is measured from the opening to the lot line, not center line of the public way
52 2015 International Mechanical Code (IMC) Example of exterior wall leakage rate 0.4 CFM/SF of exterior skin VS 5 AC/hr for allowable natural ventilation of residential units
53 2015 IMC - Continuation Enclosed Parking garages ventilation CO detectors are required to be used in conjunction with NO2 detectors 505 Domestic Kitchen Exhaust Where ducted hoods are used they should be exhausted independent of all other systems, the cleanout shall be provided at the bottom of the shaft, no offsets of ductwork in the shafts (similar to dryer exhaust)
54 Questions This concludes The American Institute of Architects Continuing Education Systems Course Rockwood Edwards, P.E. President, Cosentini Code Robert Leber, P.E. Senior Vice President Rockwood Edwards, P.E. Vice President Sr. Fire Protection Engineer, Cosentin
Objectives 2015 IBC Exit Systems Based on the 2015 International Building Code Upon completion, participants will be better able to: Determine those means of egress components that are defined as exits
2009-2015 IECC Commercial Significant Changes Summary Tier I The first change is in the layout of the book. Instead of having Chapters 1-3 that applied to all projects and then having Chapter 4 Residential
Goal 2015 IBC Update Based on the International Building Code (IBC ) The goal is to familiarize building officials, fire officials, plans examiners, inspectors, design professionals, contractors, and others
Accreditation Based on the 2012 International Building Code The International Code Council has been accredited as an Authorized Provider by the International Association for Continuing Education and Training
Applying the Building Code During Design A Step-By-Step Process AIA Learning Units The Salt Lake City CSI Chapter is a Registered Provider with The American Institute of Architects Continuing Education
Comparison of the life safety elements of the 1997 UBC and the IBC 2000. Introduction The Building Performance Research Institute s mission is primarily one of education on building safety and performance.
VERTICAL OPENINGS STUDY GROUP REPORT TO CTC MEETNG CHICAGO, IL JUNE 28-29, 2012 PUBLIC COMMENTS CTC Code Change Proposal FS50-12 was Approved as Modified as shown below - No public comments for the Group
Know Thy Codes! The Building Codes Building Codes The Code of Hammurabi 4000bc Developed 19 th and 20 th c. Codes define what you can and can t do Allowable area and height based on degree of danger Fire
Building Codes and Ordinances ARC 227 Week 6 Fire Resistive Construction 03.02.10 Instructor: Rick Staub, AIA Email: email@example.com Phone: 860-434-7707 Fire Resistive Construction Passive
Changes to the Minnesota Commercial Energy Code Presented by: Andy Thielen, PE Warning! The following is an outline of proposed code changes. There is no guarantee that the final code adopted by the State
2018 APPENDIX B BUILDING CODE SUMMARY FOR ALL COMMERCIAL PROJECTS (EXCEPT 1 AND 2-FAMILY DWELLINGS AND TOWNHOUSES) (Reproduce the following data on the building plans sheet 1 or 2) Name of Project: Address:
Class Outline Inspection of Fire-resistance-Rated Floors, Ceilings and Roofs Based on 2012 International Building Code (IBC) Introduction Determining fire resistance Test standards Definitions Alternate
Please add relevant logo here Energy Efficiency: Designing Wood-Frame Buildings for Occupant Comfort Presented by: Peter J. Arsenault, FAIA, NCARB, LEED-AP Disclaimer: This presentation was developed by
AKF Group LLC 780 CMR 9 th Edition: Major Changes AKF T A. Vernon Woodworth FAIA 3/14/17 Credit(s) earned on completion of this course will be reported to AIA CES for AIA members. Certificates of Completion
Chapter 4-16 SPECIAL DESIGN STANDARDS FOR TYPE V CONSTRUCTION Sections: 4-16-01 PURPOSE 4-16-02 APPLICABLE AREA 4-16-03 CONSTRUCTION AND OCCUPANCY 4-16-04 UPPER BUILDING AREA, HEIGHT, NUMBER OF STORIES
Code Technology Committee 2010 Final Action Agenda The following are code changes and public comments to be considered at the 2010 Dallas Final Action Hearings that are related to the CTC Area of Study
June 7, 2012 TO: PARTIES INTERESTED IN HVAC DUCT ENCLOSURE ASSEMBLIES SUBJECT: Revisions to the Acceptance Criteria for Metallic HVAC Duct Enclosure Assemblies, Subject AC179-0612-R1 (MB/CA) Dear Colleague:
Advanced Ventilation for Residential applications FBC Res 2010. Course Description Review of the Residential Ventilation requirements in the Florida Building Code, Residential 2010. I. Introduction Dean
Accreditation 2012 IBC Inspection of Fire-resistance-Rated Floors, Ceilings and Roofs Based on 2012 International Building Code The International Code Council has been accredited as an Authorized Provider
Class Outline Inspection of Fire-Resistance-Rated Floors, Ceilings and Roofs Based on 2015 International Building Code, (IBC ) Introduction Determining fire resistance Test standards Definitions Alternate
Code Requirements for Existing Buildings R. W. Sullivan, Inc. 529 Main St., Suite 203 Charlestown, MA (617) 523-8227 www.rwsullivan.com R.W. Sullivan Engineering (RWS) was established in 1945 and currently
LSE Rule Category Required Documentation Information Comments / Applicable Code Sections/ 10.1 Building Height Provide the Building height in Feet Provide the number of stories above grade Helpful Hints
Code Requirements for Existing Buildings R. W. Sullivan, Inc. 529 Main St., Suite 203 Charlestown, MA (617) 523-8227 www.rwsullivan.com R.W. Sullivan Engineering (RWS) was established in 1945 and currently
Analysis of Changes for the 5 th Edition (2014) of the Florida Codes Changes to the Florida Building Code, Existing Building This Analysis of Changes for the 5 th Edition (2014) of the Florida Codes is
Italcementi Center for Research and Innovation Bergamo, Italy LEED-NC v2.1 EAc1 A. Project Narrative (Viridian) analyzed the energy use of the proposed Italcementi Center for Research and Innovation located
I N D E X E d u c a t i o n a l S e m i n a r s f o r B u i l d i n g & R e s i d e n t i a l C o d e Title Course Number *Seminar Length (days) Pg. Class Scheduling Policies 8 International Building Code
103.2 Information required on construction documents 1. Designation of the Thermal Building Envelope on the plans 2. Insulation Material and their R Value 3. Fenestration U and SHGC values 4. Area weighted
City of Des Moines Permit and Development Center 602 Robert D Ray Drive Des Moines, IA 50309 Phone: 515-283-4200 Fax: 515-283-4270 This Code Analysis Form must be completed and returned with the Building
1 PLAN INFORMATION Residential plans must be legible and capable of digital scanning. All sheets shall be the same size and distinctly labeled with a sheet title and number. The minimum dimension of the
IMC 2012 WORKBOOK 102.3 Maintenance Mechanical systems, both existing and new, and parts thereof shall be maintained in proper condition in accordance with the original design and in a safe and sanitary
CHAPTER 4 SPECIAL DETAILED REQUIREMENTS BASED ON USE AND OCCUPANCY SECTION 401 SCOPE 401.1 Detailed use and occupancy requirements. In addition to the occupancy and construction requirements in this code,
Important Changes to the 2018 IBC for R-2 (Apartments) Green - Favorable Action for Multifamily Construction Red - Unfavorable Action for Multifamily Construction Yellow - Item of interest to Multifamily
RESIDENTIAL BUILDING REQUIREMENTS Residential Building Requirements This is an informational booklet with some of the general residential construction requirements taken from the codes adopted by Campbell
CHAPTER 7 FIRE AND SMOKE PROTECTION FEATURES SECTION 70 GENERAL 70. Scope. The provisions of this chapter shall govern the materials, systems and assemblies used for structural fire resistance and fire-resistance-rated
CHAPTER 26 PLASTIC SECTION BC 2601 GENERAL 2601.1 Scope. These provisions shall govern the materials, design, application, construction and installation of foam plastic, foam plastic insulation, plastic
Based on the 2018 International Building Code, (IBC ) The International Building Code (IBC ), establishes minimum regulations for building safety. This handout will identify important changes in the IBC
2012 Section No. 306.5 Item 2 2012 Code Information - bold text = new text found in 2012 strike out = text deleted and not found in the 2012 Equipment and appliances on roofs or elevated structures: Item
CHAPTER PRESCRIPTIVE COMPLIANCE METHOD 3 SECTION 301 GENERAL 301.2 Building materials. Building materials shall comply with the requirements of this section. 301.2.1 Existing materials. Materials already
INTRODUCTION The National Building Code of Canada (NBCC) 1 requires that some buildings be of noncombustible construction under its prescriptive requirements. Its use in certain types of buildings such
Protection of Shaft Enclosures (Exit Stairs) Protection of Shaft Enclosures (Other Shafts) Comparison on Fire Safety Provisions* (Revised 2/28/03) (S) = Small difference in fire protection, (M) = Moderate
WON-DOOR CORPORATION Won-Door FireGuard Applications A Code Analysis WON-DOOR CORPORATION Won-Door FireGuard Applications A Code Analysis THE INTERNATIONAL BUILDING CODE is widely recognized in the United
HOOD AND DUCT SYSTEMS FOR COMMERCIAL KITCHENS POLICY STATEMENT This policy applies to NEW Hood and Duct systems. The Authority Having Jurisdiction will not waive major criteria in the applicable standards
A LOOK INTO THE 2015 IECC RESIDENTIAL PROVISIONS Presented by: Shaunna Mozingo, Colorado Code Consulting WHAT CAN WE EXPECT TO SEE? Some consensus on enough is enough for now - No real roll backs, no real
Trigger (A-126.96.36.199 Existing Building Upgrade Mechanism Model) Applicability All Building Permit applications for projects related to existing buildings are required to follow the energy upgrade trigger
Disclaimer: This presentation was developed by a third party and is not funded by WoodWorks or the Softwood Lumber Board. Please add relevant logo here High Performance, Energy Efficient Design for Wood
NONSTRUCTURAL PROVISIONS FOR MULTI STORY WOOD FRAMED BUILDINGS 2010 CALIFORNIA BUILDING CODE (CBC ) Prepared for Wood Products Council WoodWorks Presented by James E. Churchill, P.E. Churchill Engineering,
Michigan Energy Code Training and Implementation Program 1.0 Hour Advanced Program Course Number 16202 Residential Energy Plan Review School of Planning, Design & Construction Michigan State University
ASHRAE 62.2: What s New in 2016 Rick Karg 2016 Residential Energy Dynamics, LLC What We Will Talk About Overview of mechanics of 62.2-2016. Logic behind the Standard. Sizing local ventilation (exhaust-only).
Fire Inspection and Code Enforcement, 7 th Edition Chapter 6 Building Construction: Components Today we will Discuss fire walls, party walls, fire partitions, and curtain walls Discuss roof types and coverings
Example LEED-NC v2.1 Energy & Atmosphere Credit 1 Submittal The following documentation provides an example submittal for the LEED-NC v2.1 Energy & Atmosphere Credit 1 (EAc1). This sample EAc1 submittal
Revised 11/29/06 Knox County Residential Building Codes Significant Changes From The 1995 CABO One And Two Family Dwelling Code To The 2006 International Residential Code All one and two family dwellings
CHAPTER 26 PLASTIC SECTION 2601 GENERAL 2601.1 Scope. These provisions shall govern the materials, design, application, construction and installation of foam plastic, foam plastic insulation, plastic veneer,
BUILDING AND SAFETY Tenant Improvement Checklist Project Address Applicant: (Please Print) Plan review Engineer: Phone: Date APPLICATION The following items will be required at the permit counter before
A Look into the The look and layout of the 2012 IECC changes Commercial Energy chapters 1-4 Commercial (CE) and chapters 1-4 Residential (RE) 2012 IECC 2011 Colorado Code Consulting, LLC 1 2011 Colorado
BUILDING CODES & DESIGN CRITERIA Adopted Building Codes: 2006 International Building Code (IBC) 2006 International Residential Code (IRC) 2006 International Mechanical Code (IMC) 2006 International Plumbing
2015 I-Code Highlights International Building Code Fire service access elevators in high rises are required to be able to accommodate a 24 x84 stretcher (size unspecified in the 2012 code). (Section 403.6.1;
2016 ASHRAE 90.1 Summary of Important Changes 1 Overview ANSI/ASHRAE/IES Standard 90.1-2016, Energy Efficiency Standard for Buildings Except Low-Rise Residential Buildings, incorporates more than 120 updates
Ontario Building Code (OBC) 1. Fire Separations 2. Fire Resistance Ratings By Classification 3. Fire Resistance Ratings By Adjacent Use 4. Fire Resistance Ratings By Specific Space 5. Fire Resistance Ratings
CHAPTER 12 INTERIOR ENVIRONMENT > SECTION 1201 GENERAL 1201.1 Scope. The provisions of this chapter shall govern ventilation, temperature control, lighting, yards and courts, sound transmission, room dimensions,
Building Inspection City of Moncton 655 Main Street Moncton, NB E1C 1E8 Phone: (506) 856-4375 Fax: (506) 856-4348 Bulletin No. 14 From: Randy Richard Date: February 9, 2015 Subject: 2010 National Building
1. Fiberboard insulation shall comply with Chapter 23. 2. Foam plastic insulation shall comply with Chapter 26. 3. Duct and pipe insulation and duct and pipe coverings and linings in plenums shall comply
HERMIT S REST GRAND CANYON NATIONAL PARK BUILDING CODE REVIEW 27 September 2007 prepared by: J. CHRIS EVANS ARCHITECT 3220 E. Terra Alta Blvd. No. 9 Tucson, Arizona 85716 520.319.8835 firstname.lastname@example.org
Bringing Outcome-Based Compliance to the IgCC September 29, 2011 Outcome-Based Codes: Any code requirement or code enforcement mechanism based on actual outcomes in buildings after they have been occupied.
CALIFORNIA COMMERCIAL BUILDING INSPECTOR CONTENT OUTLINE EXAM ID: I1 80 multiple-choice questions 3-1/2-hour time limit Open book 01. GENERAL ADMINISTRATION 6% 0101. Project Administration 1% Verify that
Pre-Inspection Checklist INTRODUCTION: This pre-inspection checklist has been produced to assist you in preparing for a Continuing Certificate of Occupancy (CCO) inspection. The inspection criteria and
Interpretation Variables and Common Areas of Confusion Of the 2009 IECC 1. (Mandatory) provisions vs. (Prescriptive) provisions: The IECC contains flexibility by allowing different approaches to achieve
CHAPTER 8 INTERIOR FINISHES SECTION 801 GENERAL 801.1 Scope. Provisions of this chapter shall govern the use of materials used as interior finishes, trim and decorative materials. 801.2 Interior wall and
2017 Commercial Building Code Wisconsin Amendments and Significant Changes Department of Safety and Professional Services Robin Zentner, P.E. Section Chief, Safety and Commercial Building Inspection Division
CITY OF MANSFIELD BUREAU OF BUILDING AND CODES 30 NORTH DIAMOND STREET 3RD FLOOR MANSFIELD, OHIO 44902 Phone (419) 755-9688 Fax (419) 755-9453 www.ci.mansfield.oh.us COMMERCIAL BUILDING PLAN REQUIREMENTS
Outcomes of ICC Tall Wood Ad Hoc Committee: Proposals and Discussion DES605 Sam Francis, C.B.O. Senior Director, National Programs American Wood Council Paul Coats, P.E., C.B.O. Southeast Regional Manager
SPARTANBURG COUNTY BUILDING CODES DEPARTMENT PLAN REVIEW CHECK LIST REQUIREMENTS FOR COMMERCIAL BUILDING PERMITS Plan Review Coordinator Kris Brannon 864-596-3180 366 N. Church St Room 500 Spartanburg,
PLANNING, PROPERTY AND DEVELOPMENT DEPARTMENT Construction requirements for LOWER LEVEL DEVELOPMENT in residential dwellings January 2018 contents GENERAL INFORMATION... 3 BUILDING CODE REQUIREMENTS...
2015 IBC Accessible Means of Egress Based on the 2015 International Building Code Description Upon completion, the participant will be able to apply the accessible means of egress provisions of Section
REScheck Software Version 4.6.4 Compliance Certificate Project RESIDENCE Energy Code: 2009 IECC Location: Perkasie, Pennsylvania Construction Type: Single-family Project Type: New Construction Conditioned
2003 International Residential Building Code Section R305 Ceiling Height Habitable rooms, hallways, corridors, bathrooms, toilet rooms, laundry rooms and basements shall have a ceiling height of not less
12-19-16 ORDINANCE NO. 3 0 32 5 An ordinance amending Chapter 59, Dallas Energy Conservation Code, of the Dallas City Code, as amended; adopting with certain changes the 2015 Edition of International Energy
Accessible Means Of Egress 2 New ADA Standards DOJ s 2010 standards (mandatory as of March 15) Based on the Board s ADA-ABA Guidelines (2004) 3 Standards Department of Transportation s ADA Standards Federal
BROCHURE # 108 CONSTRUCTION PLAN COMPONENTS Please note: This construction plan component list is to be used as a guide to assist you with your project. There may be elements unique to your project not
CHAPTER 8 CHANGE OF OCCUPANCY SECTION 801 GENERAL 801.1 Rehabilitation with no change of occupancy classification. Any rehabilitation work undertaken in connection with a change of use that does not involve
3. Assembly areas that are accessory to Group E occupancies are not considered separate occupancies except when applying the assembly occupancy requirements of Chapter 11. 4. Accessory religious educational
Interior FRT Wood References to ICC Building Codes Table of Contents International Building Code (IBC) 1 International Residential Code (IRC) 6 International Mechanical Code (IMC) 7 INTERNATIONAL BUILDING
FS103 06/07 715.3 (New), 715.3.1 (New), 715.3.2 (New), 715.3.3 (New) Proponent: Kate Steel, representing Fire & Safety Glazing Council Add new text as follows: 715.3 Classification of glazing material.
Chapter 1 101.1 Title. These regulations shall be known as the North Carolina Energy Conservation Code as approved by the North Carolina Building Code Council on March 11, 2008, to be effective January